National Grid (NG) had initially commissioned LSTC to conduct a feasibility study and outline design for a generic steel lattice full line tension (FLT) gantry. Subsequently, LSTC has been instructed to undertake further detail design and produce construction drawings. As part of an initiative to improve visual impact, NG aim to use this design on numerous Major Instructure Development (MID) projects and may be as a generic design for other projects.
LSTC developed an outline and detailed design of steel lattice type structure to carry heaviest conductor system of triple 700mm2AAAC Araucaria conductor. Two different designed provided, 26m and 22m widths, to offer the maximum flexibility for different phasing arrangements to suit all 400kV tower suits. Various exercises undertaken to identify the optimum design to suit different phasing arrangements.
To design and detail this structure, we had to maintain non-standard internal clearances to NG standards under a long span of 265m and maintaining 30°maximum angle of entry for phase conductor. Height of the FLT gantry was also restricted to the substation standards. Providing flexibility for conductor attachment catering for two conductor system, i.e. 3 x 700mm2 AAAC Araucaria conductor and 2 x 850mm2 AAAC Redwood. Overall foot print was smaller than expected for this type of structure.
Project Outcome / Deliverables
This project was completed on time and within the budget. NG is deploying this structure on the Hinkley project initially. FLT gantry structure is hugely cost beneficial for NG as compared to other tubular type gantry available.